MVHR Unit Selection
MVHR systems should achieve a leakage classification of Class 2 or better as defined in IS EN 13141-7. The unit should be certified and appear in the SAP Appendix Q list. This list contains all of the approved units for use with DEAP.
MVHR System Operation
MVHR systems are designed to run continuously. It is important that the occupier of a home understands the importance of the use and
operation of the system.
Controls for Mechanical Extract systems and Mechanical Heat Recovery Ventilation
systems should be suitable for continuous operation and should provide indication to the occupant that the system is operating correctly.
Controls should also indicate if a fault has occurred on system or if maintenance is needed.
Sizing of MVHR systems
An MVHR system should be capable of providing adequate general ventilation at all times and of meeting requirements for extract ventilation that may need to be met from time to time. The sizing is a three step process:
1. Calculate the general ventilation rate
Part F of the Building Regulations requires that the general ventilation rate should be the greater of:
a) 5 l/s plus 4 l/s per person, e.g. 25 l/s for a five person dwelling
b) 0.3 l/s per m2 internal floor area, e.g. 30 l/s for a 100 m2 dwelling.
It is likely that the requirement will be determined by method (b) in most cases.
2. Apply the adjustment for air infiltration
The adjustment for air infiltration must be deducted from the general ventilation rate. This deduction is calculated as follows:
0.04 x V (l/s), for dwellings of more than 1 storey
0.06 x V (l/s), for single storey dwellings
V is the gross internal volume of the dwelling in m3.
This figure is subtracted from the calculated general ventilation rate to give the minimum capacity of the MVHR system.
3. Check the extract rate
In order to meet extract requirements, the system may require a higher extract or boost capacity depending on the number of wet rooms (kitchens, bathrooms, etc.). The extract rate to be provided for each wet room is specified in the table below.
MVHR Systems: Minimum extract rates for Wet Rooms
| Wet Room || Minimum extract rate (l/s)
|Toilet (no bath or shower)
The required overall extract rate is calculated by adding together the relevant individual extract rates specified in the Table. If the result proves higher
than the calculated minimum capacity, the system should be capable of meeting the higher extract rate or boost capacity.
An air supply should be provided to each habitable room.
Extract will be required from all wet rooms. The system should be capable of an extract rate from each wet room at least equal to that specified in the Table above.
Transfer of air and cross ventilation between rooms should be possible. This will normally be provided by a 10mm gap under doors
A facility for purge ventilation should be provided in all wet rooms.
This can be provided by means of an opening window or external door. The area of the opening part should be at least 5% of the floor area of the room.
It is also permissible to provide purge ventilation by means of a 15 minute overun of the background ventilation. In the case of a MVHR system this can be achieved using an extract grille fitted with an occupancy sensor and timer.
In the case of a kitchen, utility room or bathroom without WC, control by humidistat is acceptable as an alternative to the 15 minute overrun.